Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Boiler over filled
Issue---Just realized our boiler was over filled. We have an automatic low water cut off which I had removed and cleaned this past fall, along with draining and flushing the 3 year old wet return. I drained the boiler until the low water cut off light was activated, waited through the delay and watched it fill to the normal level and shut off like it should. I pride myself in keeping a close eye on my system and it's maintenance, but must admit this one has slipped by me. Questions: 1) Can these cut offs operate sporadically? 2) What should I be looking for?
is there a leak in the water feed.. ? listen to the pipe that feeds from the water feed
into the boiler. You might hear the water running.0
Could you have a slow condensate return? The automatic water fill should have an adjustment for condensate return time IIRC. If this has changed for some reason, then perhaps the low water triggered the auto fill, which did not give sufficient time for condensate return, filling it to proper level, which then got raised when the condensate came back after...
Just a thought-
Did it go wonky
right after you worked on it, or did it wait a while?
I'd be very suspicious of a leak somewhere, like in the valve in the autofill. For that matter, some autofill piping arrangements have (they all should have, but...) a bypass manual fill. Could that be leaking, or the valve joggled open a bit? Try shutting off the water to the autofill and the bypass, if you have one, and see if the level is stable. If it rises, at least it isn't either of those -- and you need to figure out where else water can get into the boiler. A domestic hot water coil, perhaps?
If it is, then turn the autofill back on and see if the level holds.
In my experience, slow condensate return usually doesn't just happen all of a sudden, but builds up as a problem rather slowly. Robbie's comment has merit, though -- if there is a time delay on the autofill, could that have gotten changed?Br. Jamie, osb
Building superintendent/caretaker, 7200 sq. ft. historic house museum with dependencies in New England0
Boiler over filled
Thanks for all the responses! The overfill has only happened the one time prior to my post, and has shown no issues since. I'm keeping a close eye on it and will look into the other suggestions. Thanks again!
This discussion has been closed.
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 772 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 625 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 19 Recall Announcements