Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
I would definitely use a staging control. You can have first boiler secondary circ run as stage one to extract any heat prior to firing, stage two as the on/off boiler, then stage 3 the second boiler circulator and then stages 4 & 5 on the staged boiler. Peak performance and efficiency. Use a good controller like a Tekmar or equal to do the work. Wirig will be fun but can be done.