Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Running a forced hot water heat loop on a steam boiler.
There should not be an auto feed to the new system. The boiler is still a steam boiler? The feeder should be set up just like it always was. You need to maintain the water level in the sight glass. Once the hot water loop is purge of air, it will stay full of water.
Dave Stroman, Denver
To Learn More About This Professional, Click Here to Visit Their Ad in "Find A Professional"