To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
hey everyone I got called to a no heat call.... the customer was having problems with her bathroom not heating. some knucklehead removed a radiator that was attached to a monoflo system.... and attached 80 feet of half inch radiant tubing obviously it does not heat.... my question is that I read in one of Dan's books I do not remember which one that I can install a circulator pump on the supply-side of the branch piping to the radiant tubing...(original installers used two monoflo tees to divert water to this radiator) and wire the pump with the system pump so on a call for heat both pumps will run....and I will be using a mixing valve before pump to lower water temp....can I do this? And will this work? I know the temperature control will not be good thanks Paul s