To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Trianco Mark II M2 100 start up problems
I have a this boiler that starting having problems last year with igniter not working. I pulled the igniter out and found black soot falling out. Then it started to flameout. I cleaned the combustion chamber out with a wired brush and vacuumed.Previous owner said he never cleaned it out.
I also replaced the burner(flameholder) cause it had a few cracks in it and replaced the gas valve as a precautionary. It worked fine for 2 weeks and now it has a start up problem. It cycles through a few times then the Red Flame light on the control board starts flashing. I take power off for 10-15 seconds & with the timer off and it starts right up and works great for a few days.
I replaced the igniter, no more soot or particles falling out of the combustion chamber and set the timer back 4 minutes.
On a cold start the igniter reads 54 ohms with a current draw of 3.8 amps.
On a warm start the igniter reads 68 ohms with a 3.8 current draw. The gas valve reads approx. 25v across.
The stack switch seems to operate normal.
I sealed the gas flue with speed tape.
I have a pressure diff sw on order cause its leaking water at the housing.
Could some lend a hand in my troubleshooting?