To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Wonering what the thoughts are on adding a small say 10 gallons tank in series with my radiant on the return side of the radiant loop after the mixing valve .What i plan is to add some volume to the radiant system being it is not doing a large rea say 800 sq ft and the boiler does mod down but does seem to slightly short cycle at the end of the cycle .I was thinking that a little bit more volume would give me a bit more run time and cut the minor short cycling at the end of the cycle .I only have this slight issue with the radiant and it only occurs when it is only the radiant calling when my panel rad zone is on all is fine .Thanks peace and good luck clammy