To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Constantly purging air in hydronic system
I keep having to purge air from one of the 2nd floor circuits of my hot water heating system in order to get adequate heat out of it: I purge the system, then several days later I hear gurgling (although the noise "seems" like its coming from a different circuit upstairs), then the heat output starts to diminish in the convector over time. I bleed and everything's fine for a week or so. Let me give you details of my system...
I have a pump circulated hydronic system (circa 1950's) in my old colonial (circa 1910's). The boiler is a gas fired (80,000 BTU?) 80% efficiency New Yorker unit (circa 1990's) and the house is ~1,300 sq.ft. There is a single pump on a single zone feeding all circuits which have a mix of newer baseboard radiators (living room & bathrooms) and original-to-the-system fan-coil hydronic convectors (bedrooms, dining room, kitchen). The electrical circuits for the hydronic convectors, however, are split into two zones: 1st floor convectors on one thermostat & 2nd floor convectors on the other.
All the radiators/convectors on both floors have manual air purge valves that are pretty much in useless condition. As such, after I moved in, I had a good plumber/heating guy install shut-off and boiler drain valves in the return risers of each radiator/convector in the basement for easy purging. At the same time, he installed a city water make-up pressure-regulating device set to ~15psi, an automatic air purger (w/automatic purge valve) on the supply side of the boiler, and finally he re-routed the expansion tank to the supply-side. In addition, there is one automatic purge valve in the baseboard of one room upstairs that was there when I moved in (not the unit that needs constant purging, though). There is a file attached showing the layout of my system as I know it (there is only one shut-off/boiler-drain valve shown on the bathroom loop, but they are actually installed on every circuit in the basement risers).
My question is, where is the air keep coming from? I don't see any signs of leaking water anywhere in the system? Could it be air coming in from the city water makeup and there's nothing I can do about it? Any help would be appreciated.
Oh, one less important side question: The boiler is running with a Honeywell L8148E1265 aquastat and it's set at it's lowest setting = 180degF. However, I noticed that it very rarely (only really cold days here in SE Michigan) gets to kick off at it's 195 upper set point (15 deg differential). Would I benefit from lower set point aquastat (say, a Honeywell L8148E1299) or should I leave the system as designed?
0 · ·