Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
The near boiler piping is squeezed between the indirect and boiler its tight.I'm thinking of locating the expansion tank where ever i can fit it and connecting it from there to just after boiler supply and upstream of the pumps.
My question is do i need to worry about the elevation of tank relative to where it ties in to supply? i know more than a couple feet might change pressure, but im more wondering if i can hang it higher and pipe up then down to top of supply or at same elevation and pipe into supply from side.
Also Im using the discaldirtmag so its not able to go into bottom of airsep.
putting the dicaldirtmag on the return just before boiler where manufacturer shows a strainer,instead of the supply, This spreads out some of the accessories, do you think thats really bad idea?
If i can squeeze it on to the supply is the expansion tank connection best before or after the discaldirtmag ?
thanks guys siggs a bit vague about just how remote you can go with the tank
If i came up off the tank and then back down into top of supply line should i use a tee with vent on top of tank?