Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
I saw this the other day. This is a district heating system and the steam is being controlled by a modulating steam valve feeding 2 coils in a Airhandler. The bottom coil’s F&T trap’s outlet is obviously below the condensate line. The steam pressure being fed right before the valve is between 12-15 psig from what I saw. There are no gauges on the condensate return side to see what the actual pressure is at the trap. I was just wondering what you guys think about it.
Is there a specific reason it runs at 12-15 psi? Is it a high lift? Specific equipment requirements? Or someone just jacked it up? Just curious 🤔? Mad Dog 🐕0
I don’t know exactly why it runs at such a high pressure. I have to download the manual for the equipment specifications. There are steam coils 5 stories up from where this one is and it works off the same steam pressure reducing station as this one.0
You have two choices. Experiment during cold weather and find the lowest pressure that delivers the heat you need.
Find the original specs or the engineer that designed it. Not unusual to run commercial steam at higher pressures. But the lower the pressure you can run and still deliver heat will make the system easier to control The height og the coil above the boiler makes no difference to the steam. Its strictly pipe size and load1
Ok, good info.0
You might be leery of Engineer specs.
For instance, I have a print that was made for construction use, that states to run the boilers at 15 PSI.
These boilers are fitted with 15 PSI relief valves as stated on the same print.........
They actually run at about 5 PSI.0
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.8K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 773 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 627 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 19 Recall Announcements