Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Oil Drip..... can anything be done??
We were called to a client that has an Intertherm Furnace with a Beckett gun.
It leaks oil back and eventually works it way through the casing and onto the floor.
Everything seems to have been tried. Pressure is good. There is a tiger loop on the system. We even tried a Delavan Protek nozzle. The drip keeps coming back.
The furnace is level but the gun is not even close, so it is back pitched. This is the cause that we see for that one drop at shutdown does not fall into firebox but goes back down nozzle assembly.
We have never seen anything about this. At a standstill.
Thank You for your help.