Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Patterson Kelley Mach 750
Recently had a 10 year old Mach boiler heat exchanger crack. So we did a like for like change as spaced by the customer. We had no prior history of the existing boiler which begged the question “why did it crack” ...on start up we kept getting Delta T too high, so Indicating we need more flow. Checked all strainers, air separator, valves etc.. found some small things but nothing major. Pulled pumps to make sure impellers ok and in tact. gas pressures are correct and even de rated boiler by 20% by changing inducer speed. The only information we did have is the PH reports of the 40/60 ethylene glycol which were all good. No make up water to this boiler it is closed glycol loop. Today we got a “high temp” alarm. I do have a water balance company coming to evaluate and give us a baseline to start with.
We have a 4 air handler with aqua coils that are 100% outside air. We also have in floor in concrete for perimeter heat through the whole building. I say perimeter because the in floor loops cover the entire building only 8’ in from outside walls. The center of the slab has no loops. And a lot of the piping is outside for the air handlers.
My experience with aluminum heat exchangers is that they are very touchy and heat up extremely fast. They don’t seem to want to work well with this kind of set up. Any thoughts ?
**** Forgot to mention that the boiler temp drops incredibly fast once boiler is shut down for any reason.