Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
I have an old thermostat with only 2 wires connected to my Weil-McLain CGA Series 2 boiler. I would like to replace it with a Nest thermostat. I need to add a C-Wire in order for it to work. Luckily, the cable coming from my thermostat already has a 3rd wire that I can use. I just need to find where to connect the C wire on the boiler side. In attached picture, blue pen drawing shows existing wirings. The Low Water Cut Off has 4 wires, and one is already connected to the C Common terminal. Can I just connect my thermostat’s C wire to the same terminal? (Green pen in drawing) Thanks!
Aquastat is I believe Honeywell L4006E1067. Low Water Cut Off is GuardDog LB-24E. Orange and blue nuts connectors in picture connect all the above limits + thermostat in series to the thermostat connector on boiler. All other limits and external devices are mounted per manual diagram.