Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
feeding with a MM67, new install
So I finally have a boiler with a MM67 and I need to feed it, anyone have a good-better-best way to do this? A few weeks ago I had issues with overfilling and @Steamhead gave me some tips. This is a little different- when i set up the TDC should i just change the circuit to 24V and do a 24v feeder? Running a TDC with line seems more cumbersome. Thanks for any comments
If the 67 is wired 120V, I'd use a VXT-120, add the necessary switched wire back to the junction box and run a 3-wire BX cable from there to the VXT.All Steamed Up, Inc.
Towson, MD, USA
Steam, Vapor & Hot-Water Heating Specialists
Oil & Gas Burner Service
Ok cool so yes or no on the time delay? Or, is it the SG400 that requires the TDC?0
I think I’m confused. A few weeks ago it was new style low-water cut off with oldschool Feeder, this time it’s old style LWCO with the new feeder. Got it. I’m making it more complicated than it is thanks for the advice0
- 120.9K All Categories
- 83.9K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 415 Carbon Monoxide Awareness
- 34 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 114 Geothermal
- 154 Indoor-Air Quality
- 3K Oil Heating
- 49 Pipe Deterioration
- 756 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 619 Buy, Sell, Barter
- 37 Industry Classes
- 70 Job Opportunities
- 14 Recall Announcements