Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
steam boiler with automatic vent damper
Does anyone know exactly why you cant use a power stealing Tstat such as a nest on a steam boiler with an automatic vent damper? i ran into this problem with a customer that had a existing nest which we all know is a power stealing tstat. we had no common to tsat. it worked with old weil mclan but when we put a new steam boiler in (williamson thermoflo) the tsat kept dying. we measured 13volts at tstat on wall. as well at boiler as soon as we used the switch on automatic damper to keep damper open we got 24volts in both places. we called the tech line of manufacture but they werent helpful at all in helping me understand why? all they said is you can not use a power stealing stat on their boiler with no explaination. Now im the kind of guy who has to know why , i study the electric diagram of boiler and the manual to automatic damper and neither was any help. So i was just wondering if anyone could explain as to why?. (End result was well left damper in manual open and explained to customer either he gets a new non power stealing tstat or leave the damper open and loose some efficency to new boiler.