Welcome! Here are some tips for using this forum.
no shut off between boiler and air eliminator
Hi, I'm trying to purge my system of air. It was built in the mid-70s, and for whatever reason, there are no purge valves on the baseboards. Apparently no one has thought to change this prior to us moving in. It's a three zone system, and there are no shut off valves for each zone. So, my questions are:
1. do I engage the motor to open up each zone to purge?
2. there doesn't seem to be any air popping out of the drain when I bleed. How long do I need to bleed?
3. Since there is no shut off between the air eliminator (supervent) and the boiler, will there be pressure if I attempt to change the head, or clean it?