Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
MC80 Contender Second Heating Zone wiring using built-in DHW: Questions
I have been using an MC 80 Contender a number of years now for radiant in-floor heating a finished basement walk-out concrete slab operating at 120*F max. We have just finished our upstairs of this retirement home of ours.
I want to use the DHW sensor inputs and DHW circulator pump outputs (to a 2nd, separate pump) to supply the 4-zone-valve system for the newly installed upstairs radiation (properly sized for use of 'Smith's Environmental HE-3' emitters - at the same 120*F loop supply temperature).
The in-use t-stat input is simply a contact closure, upon heating call, across open-circuit 24VAC at "Low Voltage" terminals 7 & 8; and, works well.
The proposed-to-use DHW inputs (at terminals 6 & 7, also in the "low voltage" side) are +5VDC at terminal 7 with respect to return at terminal 6. What current (I assume, in milliAmps) does this circuit supply/able to handle; maximum?
After much research, I have not been able to tell whether these DHW sensor inputs are intended for a contact closure, thermistor (what value & type - 10K @ 0*C NTC, 100K - PTC, etc., for instance) RTD (again, spec's?) or other input type; is anyone here able to answer these questions with very specific data/specifications?
I'll appreciate any/all helpful answers.