Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Ran across a 2 pipe steam system today that I could not find a trap at the radiators. The house was built in 1911. The radiators I looked at have a 3/4 pipe with a hand valve feeding the top of the radiator and a 1/2 pipe coming out the opposite side on the bottom. Could there be a group of rads on one trap?