Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Radiant for slab on grade
Hello, I am a plumber, who has installed a few radiant floors 18 years ago in my residential days, I have not been involved in any installations since then. I have been in commercial industrial for the last 15 years. I am in the process of selecting house plan for our house that I intend to build. I would like to build a slab on grade, with radiant floor. I am wondering where I should be looking for good design ideas. Also I would like to install a combination boiler to provide my DHW. Or would I be better to install an indirect storage tank? Any suggestions would be appreciated!
Where are you located Pipes ? What type of envelope construction are you planning on , typical construction or will it exceed code minimum ?
This is the place where you will get the BEST DESIGN IDEAS .
To start off with dependent on where you are and what loads you will have , forget the combi unless you plan on one with some mass .You didn't get what you didn't pay for and it will never be what you thought it would .
Langans Plumbing & Heating LLC
Serving most of New Jersey, Eastern Pa .
Consultation, Design & Installation anywhere
Rich McGrath 732-581-38330
Second that!Rich said:
forget the combi unless you plan on one with some mass .
A generous sized indirect is also great in the summer with an add on Heat Pump Water Heater (HPWH) for some cooling and dehumidification in the summer months, if your location requires cooling.
Serving Northern Maine HVAC & Controls. I burn wood, it smells good!0
Rich/SFM- Thanks! I am building in Eastern Ontario Canada. House will be constructed with 2x6 framing, with a mix of stone/wood on the exterior. I will look into the HPWH. I will require cooling in the summer months. I had planned on installing an AHU with coil for AC. I should have mentioned that I plan on installing a zero clearance fireplace as I have 200 acres of bush to get wood from. I had considered installing an OWB, but have done some research, and not sure if I want to be a slave to it!! Also I had read in some other posts about insulation under the radiant should be 4" thick. Is it worth the extra investment?
As I get closer to finalizing house plans I will have more info/questions.
Not sure about Ontario but CSA states 1" foam under slab. Honestly I think you would wise to install 2"Min for R.100
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 771 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 625 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 17 Recall Announcements