Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
New customer and CO alarm going off with new batteries installed. My Sensorcon personal CO detector registered 0 ppm when entering the home and stayed there, as did my Bacharach Monoxor. I did a combustion analysis on both the water heater and furnace and CO was less than 20 ppm on both. B-vent was unobstructed and venting well, all visible joints solidly connected. No car started in the garage, dryer or stove weren't in use, and no fireplace. Advised her to get a new low level CO alarm.
Tell me I can't, and I'll show you I can.