Welcome! Here are some tips for using this forum.
Condensation in the chimney
Many of you have read or responded to past posts; thanks.
My new Megasteam 513 is now running well; 13 CO2, no smoke, about 335*F at the breach. But draft is -0.05 at the breach and +0.02 over the fire.
Now it is dripping condensate down the wall and onto the floor from the chimney cleanout. At first, I thought it was just melted snow or rain (need a new cap), but it is still happening with clear skies.
I'm considering removing the baffles, to see if this will raise the temp, and improve the draft, and reduce the condensation.