Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Just ran a service call non a system I installed in 1999
I haven't done much refrigeration in the last six or seven years but the customer called a week ago and then again yesterday and was desperate. It's a beer and wine store and so naturally his busiest week and the walk in cooler was down. When I arrived he told me he had the compressor replaced last week and it was still not working. I found the original dryer in the system, the cap tube from a replaced condenser fan cycle control still connected to the discharge line. Recovered what was left of the charge and replaced dryer removed cap tube evacuate weigh in charge. Start up and found that the electronic TEV [ Becon one system ] had no voltage. Replaced evap in and out sensor cost $14.00 each. Box was at 48 and drooping like a rock when I left 75 when I arrived. I thought I was gonna get my first kiss from a man from India. Asked the owner if the other two tech's had even asked for the book that I left on the job and he said no.