Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
SubCooling per floor of a house.
Getting a little progress done. One chart shows SC per 10' of riser.
10'=4.9psig drop=1.6*f temp drop(SC)
20'=9.7psig drop=3.1*f temp drop(SC)
30'=14.7psig drop=4.7*f temp drop(SC)
LL/FD = 4' of copper SGMI=3' LLSV=5'
1/2" 90* ell , long radius = 1' of copper
another chart is slightly different , 10' of rise is 2* of SC and 5* of SC at a 30' rise