Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
new piping ..is it right now?
My burnham pin 4 steam boiler is being repiped for the 3rd time.They are getting rid of the bullhead tee finally (see photo 1).Any opinion on how they are planning to connect the mains off the header and equalizer(see photo 2)I want to be sure it is piped correctly this time. Is this long nipple and the 2 pipes going up to the 2 separate mains O.K?They checked measurement on the header it is at 24 minimum from water line. Still insisting copper is ok above water for the returns. How should the hartford loop be configured now with the new piping? Can not tell you how much I appreciate all the great help I been receiving from this Wall...I'm just a homeowner who has had to learn as much as I can about steam since having so many problems with this new install in November.