Welcome! Here are the website rules, as well as some tips for using this forum.

# Multi-unit house Electric Radiant Floor or Forced Air/Gas?

Member Posts: 1
Hi, I am a homeowner in the middle of renovating a 2 unit rowhouse to a 4 unit house. The house shares walls with a house on either side (except for new top floor which we just added). It used to be heated by forced air fueled by gas. Each unit is sq ft is 600, open living area and 2 (tiny) BR and bathrooms. The ceilings are 12ft. We will have gas stoves and a gas fireplace in each unit.

I really want to use electric floor radiant for all units but I have discovered that the per unit price of electricity in the area is 3 times as expensive as the per unit cost of gas. I want to figure out whether the fact that electric floor radiant heats the most relevant area ie near the floor where people are, means that even if it is more expensive per unit bc fewer units are used than with forced air where the air has to be pushed from the ceiling down, whether it might be cheaper in the end to use electric radiant floor heating.

Can you help me figure it out? Ie most effective and coat efficient way of heating 600sq ft with 12ft ceilings? We are hanging drywall now so I have to figure this out ASAP help!:)

• Member Posts: 7,356
What's under the floor?

any way to put tubing and plates up from below?

Radiant heating will require a bit less energy than forced air, all things being equal.  You can generally count on a space temp (air) of 3º-4ºF lower, but the BTUs still need to be there to offset the losses.

http://www.eia.gov/neic/experts/heatcalc.xls will help with the math.
• Member Posts: 2,766
edited November 2013
Math

1 Kw = 3,414 BTU

1 Therm = 100,000 BTU

These are both billing units used by utilities . If 29.3 Kw of electrical energy costs less than 1 therm I think you have your answer .  Where I am in NJ the Kw costs .14 and the therm costs .52 .  So here , in this market my choice would be between 4.10 and .52 . or 8xS more expensive for electric .
You didn't get what you didn't pay for and it will never be what you thought it would .
Langans Plumbing & Heating LLC
732-751-1560
Serving most of New Jersey, Eastern Pa .
Consultation, Design & Installation anywhere
Rich McGrath 732-581-3833
• Member Posts: 7,356
Don't forget

to include appliance efficiency in those numbers.  That DOE spreadsheet is really handy.
• Member Posts: 9,546

Radiant needs to be planned for.

If your only options at this point is scorched air or electric radiant, I would opt for the forced air with electric radiant as a floor warming asset to say a bath area.

To heat solely with electric radiant would cost an arm a leg, and first born at those rates.

Keep in mind your choice of floor coverings. Low r for radiant areas. If the kitchen is tiled, and the bath use the electric radiant as floor warming in those areas leaving the actual heating to forced air.

Depends a lot on your expectations here. Is duct work existing or needing redesigned?

What was there before?

IF you really want radiant do it hydronically not electrically.

With hydronics you are unlimited in heat source choices in the future. With electric... Well it's electric.

Are you wanting AC? If so duct work is in the picture anyway along with air handler etc.
• Member Posts: 7,356
For that small an apartment

I'd seriously consider these http://www.rinnai.us/direct-vent-wall-furnace before I installed ductwork.
• Member Posts: 9,546
Right

But what about Ac Kurt?
• Member Posts: 7,356
If A/C is part of the requirement

and the owner of this rental property places some value on ROI,  I would probably recommend a multi-head ductless mini-split like the Mitsubishi CITY MULTI, the Daikin VRV, or the Fujitsu Halcyon.
• Member Posts: 1
Security Seal Facebook Twitter GooglePlus Pinterest Newsletter Sign-up all news News Bosch Plans to Form Joint Venture with Carrier to Develop and Manufacture Geothermal and Water-Source Heat Pumps Robert Bosch North America Corporation and Carrier, the w

Hi everyone. Thanks for your answers. Homeowner again. Just to clarify,

The apartments are actually 980 sq. ft.  The 600 sq ft mentioned is

covered area for the heated floors.  Ducts are already in place for A/C and each unit is wired for gas stoves and a gas fireplace in the living area.

Because the ceilings are 12 feet high I worry about the forced air

system heating the upper 6 ft of height while we freeze on the sofa.

A comparison shows that electric is almost 3 times the price per 1mil BTU’s of gas based on local pricing.

I have noticed that there are slim (less than an inch

high) hydronic radiant systems in the UK and Europe which would probably

work for my renovation.  But I have not seen the equivalent here in the

US.  Does anyone have knowledge or experience with anything like this?

It seems I can use a boiler and slim tubing to heat my property, if I could locate them.

I am considering tankless hot water.
• Member Posts: 9,546
All kinds

Of over the top sandwich radiant.

Warm board r

Raupanel

Roth panel

Quick track wisbro

Or make your own plywood sandwich sleepers.
• Member Posts: 7,356
electric is almost 3 times the price

a heat pump produces 2-3 kW of heat for every kW of electricity that it consumes.  The exact number depends on the particular heat pump (more expensive models generally have higher efficiency) and the outdoor air temperature at the time.
This discussion has been closed.