Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
hey everyone.... I have a job in NYC that has been giving us a problem for a long time its a split 410 a system. with the condenser and air handler side by side condenser discharge in and take are ducted I have a high side pressure of 400 psi and a low side pressure of 135 psi my super heat is 2 degrees and subcooling 16 degrees the problem is the low-temperature split which is 12 degrees I am pretty stuck on this job and don't know where to go from here the customer says that this is always been a problem... thank you Paul S
ASM Mechanical Company
Located in Staten Island NY
Servicing all 5 boroughs of NYC.