Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Cat 1 vs Cat 3 - benefits to Cat 3?
Cat 1 appliances are mid efficient non positive vent pressure - non condensing. Cat 3 are mid efficient positive vent pressure, non condensing. If an appliance can run either option (e.g Viessmann Vitorond 200), what benefits are there to running a cat 3 over a cat 1? The only one I now know of is you can run smaller vent sizes on Cat 3 obviously because the positive vent pressure helps push the flue gas out instead of relying on draft to move it. The cat 3 may be slightly safter as it has to be a fully sealed vent where as a Cat 1 in a lot of cases requires some form of draft control (e.g. draft hood, barometric damper) which could spill in some situations. Any other benefits to Cat 3?
Class 'A' Gas Fitter - Certified Hydronic Systems Designer - Journeyman Plumber