Click here to Find a Contractor in your area.
Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
American Standard condensing propane furnace lockout issues
We installed an American Standard warm air furnace in a customers home about five years ago. The system ran fine for years and then...this year has had nothing but lockout issues. The fault code comes up as a 2-flash which is (3 unsuccessful tries for ignition). We verified correct inlet gas pressure-12"WC, correct manifold pressure-6"WC first stage and 10"WC second stage. When fired, the pressure drop is not more than 1.25"WC. Flame signal is 2 micro amps. The primary heat exchanger was cleaned, the fresh air pipe disconnected, the pressure switch closes at he proper settings. The flame sensor was replaced along with the circuit board to try to eliminate grounding issues but still the same thing. The propane tank was filled in the summer and just recently filled again late February. Maybe I'm missing some thing obvious here but what else should I be checking?
This discussion has been closed.
- 115.1K All Categories
- 82K THE MAIN WALL
- 2.6K A-C, Heat Pumps & Refrigeration
- 38 Biomass
- 397 Carbon Monoxide Awareness
- 1.5K Domestic Hot Water
- 4.1K Gas Heating
- 102 Geothermal
- 145 Indoor-Air Quality
- 2.6K Oil Heating
- 37 Pipe Deterioration
- 630 Plumbing
- 4.6K Radiant Heating
- 342 Solar
- 12.7K Strictly Steam
- 2.8K Thermostats and Controls
- 44 Water Quality
- 571 Buy, Sell, Barter
- 29 Industry Classes
- 62 Job Opportunities
- 11 Recall Announcements