In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.

Member Posts: 1
what will happen when you under size your boiler header have a boiler with 2 5inch risers off of boiler they go into a 6inch header boiler manufacure wants a 8inch header

• Member Posts: 11,321
You'll have a LOT of problems

wet steam, high fuel consumption, uneven heat, banging, water-level problems in the boiler........

Do it right. Change the header.
All Steamed Up, Inc.
"Reducing our country's energy consumption, one system at a time"
Steam, Vapor & Hot-Water Heating Specialists
Oil & Gas Burner Service
Baltimore, MD (USA) and consulting anywhere.
https://heatinghelp.com/find-a-contractor/detail/all-steamed-up-inc
• Member Posts: 252
yea

u got to do what the manuf. want if u ever have problems down the road, but 8" does seem excessive. 2- 2.5" pipes don't even come close to 1- 6" flow rate, so what is it based on?
• Member Posts: 181
That's 2) 5" risers,

which makes sense for an 8" header. Must be a pretty large building...
• Member Posts: 3,911
wet steam poor heat

2.5 x2.5x 3.1416x2 = 39.27

3x3x3.1416= 28.27

4x4x3.14=50.26

Cost is what you spend , value is what you get.

cell # 413-841-6726
https://heatinghelp.com/find-a-contractor/detail/charles-garrity-plumbing-and-heating
• Member Posts: 181
I agree with your conclusion Charlie,

but not sure I understand what you mean by your math. Can you explain further please?
• Member Posts: 252

this is my math, if i'm wrong i need to know where

the radius of a 2.5" pipe is 1.25"          and the radius of a 6"pipe is 3"

1.25x1.25x3.14=4.90sqin +                        3x3x3.14=28.26sqin

1.25x1.25x3.14=4.90sqin

= 9.8sqin

i can't get it to stop underlining!!!   but i'm pretty sure that u add the area off the two 2.5" risers to get the tottal area of the two, but if i'm wrong and you multiply them together it's still only 24.01sqin.
• Member Posts: 181
Oh, I think I get what you're saying Charlie...

The area of (2) 5" risers is Pi*Rsquared = 3.14*2.5squared, times 2 risers = 39.27

The area of the current 6" header is PiRsquared = 3.14*3squared = 28.27, which is too small

The area of the spec'd 8" header is PiRsquared = 3.14*4squared = 50.26, which is larger than the total area of the 2 5" risers.

The minimum header size would be slightly larger than 7", which means you need an 8" header.
• Member Posts: 3,911
it is two 5" risers pipeking not

two 2 1/2" risers. we are in the big leagues now boys.
Cost is what you spend , value is what you get.

cell # 413-841-6726
https://heatinghelp.com/find-a-contractor/detail/charles-garrity-plumbing-and-heating
• Member Posts: 7,356
and you can drop the π

anytime you are comparing round pipes.  Squaring either D or R will give you the answer.
• Member Posts: 3,911
I kept in Pi to show

the actual area diffrence not ust the proportional  difference. If the numbers differ by larger amounts it seems to make the problem more visible. When comparing in my head I leave out the Pi. Unless it is right after supper then I have the pie if it is there to be had.
Cost is what you spend , value is what you get.

cell # 413-841-6726
https://heatinghelp.com/find-a-contractor/detail/charles-garrity-plumbing-and-heating
• Member Posts: 252
I NEED GLASSES!!!

i could have swore it said " how would u size a boiler with 2.5inch risers" i thought there was a decimal point.!! you got it, whoaoawhoa, you got it!! we're in the big leagues now!
• Member Posts: 181
Good point...

multiplying all variables by the same constant does just give you more messy math. I hadn't really ever thought about it.

I'm kind of anal though, and I think seeing the real numbers, not just proportional numbers, somehow makes me happier, whatever that means.

• Member Posts: 3,911
edited February 2013
Pie for dinner

Pot pie or Steak and Kidney? The kidney in steak and kidney pie is beef kidney not kidney beans so you should be good.
Cost is what you spend , value is what you get.

cell # 413-841-6726
https://heatinghelp.com/find-a-contractor/detail/charles-garrity-plumbing-and-heating
• Member Posts: 181

can't do kidney beans... but pot pie is all good
This discussion has been closed.

Welcome

It looks like you're new here. If you want to get involved, click one of these buttons!