In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
The results were much better than expected; it replaced a waaaaaay oversized UPS32-160F. You could hear it howling like a ghost throughout the entire building and there was no delta T on the supply & return. I gave them a quote on replacing it last winter but they said it was out of their budget at the time, it finally crapped out after about 4 years in service about 3 weeks ago so it became a necessity being a town hall in a small hamlet about an hour away from my own. I generously estimated the head of the system at 16ft. @35gpm but it turned out to be much less than that as you can see in the pic. It's pumping through 1-1/4" convectors in wooden cabinets throughout the approx 10,000 sq ft building. It usually draws less than 32watts and has cost about $2 to run over the last few weeks, compared to the old circulator's 625watts (on speed 3 which is what it was on lol!) I figure they'll have a yearly savings of about $300.