Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Take offs looped together
Should two take offs out of the header loop aroud the basement and eventually join? The two farthest radiators from the boiler don't get hot and would be easy to isolate the two take offs so they have the same load.My house is two pipe with no main vents and only vents on the radiators.I've been talking to a contractor to install main vents so I can get rid of the raditor vents.