In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
i got a goodman aepf42 16seer air handler one year old that customer stepped on condensate drain and stressed pan connection which made a big crack. my question is on a horizontal set up and i need to change out horizontal pan can i swing out evaporator coil with piping still connected and not have to pump down and cut open system?i was thinking of loosening clamps and trying this first. goodman says i have to pull coil to get pan out as it sits in pan. i have done other styles by just wiggling the pan from under the coil and sliding it back under. so i am wondering if anyone has done this particular goodman before... thx