Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Modulation Range - Burnham Alpine
Chotu Member Posts: 14
Per the I/O manual - Burnham Alpine 150 Boiler modulates between 30 to 150 MBH input. Is it possible to have it modulate, lets say between 10 to 150 MBH? Perhaps via the Gas Valve (Dungs GB-WND 055) throttle adjustment. I have a small zone and would like the boiler to modulate down to meet its small heat demand with minimal cycling.
The modulation range of negative pressure gas systems is determined by the minimum allowable fan speed. Most of the fans can't be run below 20% of full HZ. Thus the industry standard of 5 to 1 turn down ratios.
IBC had a boiler with a 10 to 1 turndown, but I am not sure what they were doing different.
A buffer tank or true hydronic separation is your best option.0
This discussion has been closed.
- 120.9K All Categories
- 83.8K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 415 Carbon Monoxide Awareness
- 34 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 114 Geothermal
- 154 Indoor-Air Quality
- 2.9K Oil Heating
- 49 Pipe Deterioration
- 745 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 619 Buy, Sell, Barter
- 37 Industry Classes
- 71 Job Opportunities
- 14 Recall Announcements