Welcome! Here are the website rules, as well as some tips for using this forum.
Another one bites the dust!
Finally figured out why 8-10 compressors have died and 2 brazed plate heat-x ruptured.Repaires/replace have cost/will cost a LOT!!!!!! Each comp is 15 ton. The chilled water loop is good for 260GPM and the 10 compressors require 450GPM. Go figure! Now, the "fix em' up time" is here! This is a new customer to me,they HAD problems w / the Chilled Water. WHAT A RUSH I GOT !!!!!!!!!