Welcome! Here are the website rules, as well as some tips for using this forum.

If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.

# High Velocity Variability

Member Posts: 57
I recently had installed two high velocity air conditioning systems, one for the first floor and basement and the other for the second floor.  I noticed some variability in the velocity of the air flow coming from the outlets so I bought a wind meter and measured the velocities of all the outlets.

My measurement technique was to stand the meter off the outlet with a 3/4" block and take a measurement.  My objective was to measure the air flow velocity as close as possible to the outlet while impeding the flow as little as possible.  I used a 3/4" block instead of holding the meter freehand to improve repeatability.  While these measurement may not be valid absolute velocity measurements, I think they are valid relative velocity measurements that can be use to compare one outlet to the next.

The downstairs and basement system is a 2 1/2 ton Spacepak unit with 15 outlets.  The maximum velocity was 7.2 meters/sec, the minimum was 4.1, the average was 5.3 and the standard deviation 1.0.  The slowest outlet had 57% of the velocity of the fastest.

The upstairs system is a 2 ton Unico unit with 12 outlets.  The maximum velocity was 8.6 m/s, the minimum was 5.5, the average 7.0 and the standard deviation 1.2.  The slowest outlet had 64% of the velocity of the fastest.

In comparing the upstairs and downstairs systems, the upstairs system has velocities about 1.5 m/s faster than the downstairs system.

Does any of this matter?  I am concerned about these variations and the difference between the upstairs and downstairs systems, but in the middle of the summer all I care about is if the system meets its design spec of 75 degrees inside at 95 outside.  I live in a relatively well insulated three bedroom colonial near Boston.

Thanks.