**Welcome! Here are the website rules, as well as some tips for using this forum.**

Need to contact us? Visit https://heatinghelp.com/contact-us/.

**Click here to Find a Contractor in your area.**

# High Velocity Variability

JohnG_3
Member Posts:

**57**
I recently had installed two high velocity air conditioning systems, one for the first floor and basement and the other for the second floor. I noticed some variability in the velocity of the air flow coming from the outlets so I bought a wind meter and measured the velocities of all the outlets.

My measurement technique was to stand the meter off the outlet with a 3/4" block and take a measurement. My objective was to measure the air flow velocity as close as possible to the outlet while impeding the flow as little as possible. I used a 3/4" block instead of holding the meter freehand to improve repeatability. While these measurement may not be valid absolute velocity measurements, I think they are valid relative velocity measurements that can be use to compare one outlet to the next.

The downstairs and basement system is a 2 1/2 ton Spacepak unit with 15 outlets. The maximum velocity was 7.2 meters/sec, the minimum was 4.1, the average was 5.3 and the standard deviation 1.0. The slowest outlet had 57% of the velocity of the fastest.

The upstairs system is a 2 ton Unico unit with 12 outlets. The maximum velocity was 8.6 m/s, the minimum was 5.5, the average 7.0 and the standard deviation 1.2. The slowest outlet had 64% of the velocity of the fastest.

In comparing the upstairs and downstairs systems, the upstairs system has velocities about 1.5 m/s faster than the downstairs system.

Does any of this matter? I am concerned about these variations and the difference between the upstairs and downstairs systems, but in the middle of the summer all I care about is if the system meets its design spec of 75 degrees inside at 95 outside. I live in a relatively well insulated three bedroom colonial near Boston.

Thanks.

My measurement technique was to stand the meter off the outlet with a 3/4" block and take a measurement. My objective was to measure the air flow velocity as close as possible to the outlet while impeding the flow as little as possible. I used a 3/4" block instead of holding the meter freehand to improve repeatability. While these measurement may not be valid absolute velocity measurements, I think they are valid relative velocity measurements that can be use to compare one outlet to the next.

The downstairs and basement system is a 2 1/2 ton Spacepak unit with 15 outlets. The maximum velocity was 7.2 meters/sec, the minimum was 4.1, the average was 5.3 and the standard deviation 1.0. The slowest outlet had 57% of the velocity of the fastest.

The upstairs system is a 2 ton Unico unit with 12 outlets. The maximum velocity was 8.6 m/s, the minimum was 5.5, the average 7.0 and the standard deviation 1.2. The slowest outlet had 64% of the velocity of the fastest.

In comparing the upstairs and downstairs systems, the upstairs system has velocities about 1.5 m/s faster than the downstairs system.

Does any of this matter? I am concerned about these variations and the difference between the upstairs and downstairs systems, but in the middle of the summer all I care about is if the system meets its design spec of 75 degrees inside at 95 outside. I live in a relatively well insulated three bedroom colonial near Boston.

Thanks.

0

## Comments

This discussion has been closed.

#### Categories

- All Categories
- 86K THE MAIN WALL
- 3.1K A-C, Heat Pumps & Refrigeration
- 52 Biomass
- 421 Carbon Monoxide Awareness
- 81 Chimneys & Flues
- 1.9K Domestic Hot Water
- 5.3K Gas Heating
- 96 Geothermal
- 154 Indoor-Air Quality
- 3.3K Oil Heating
- 60 Pipe Deterioration
- 893 Plumbing
- 5.9K Radiant Heating
- 379 Solar
- 14.7K Strictly Steam
- 3.2K Thermostats and Controls
- 52 Water Quality
- 41 Industry Classes
- 47 Job Opportunities
- 17 Recall Announcements