Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Puff of Smoke from top of Boiler
ACG Member Posts: 8
in Oil Heating
I have a weil mclain SGO 3 oil boiler. My flue pipe is connected in the rear of the boiler. Every so often, perhaps once a week or once every 2 weeks, the boiler will be running through a cycle or trying to, and then the damper will flap a few times and then grey to black smoke will puff out of the top of the boiler, causing the collector hood and flue cap to pop up slightly. The smoke is not continuous, just a single puff, enough to stink up the basement but not enough to set off a fire alarm or carbon monoxide detector.
Any idea what may cause this?
Any idea what may cause this?
Call a pro NOW!
Looks like this has been going on for a way to long. I'm not a pro but could be a number of things like a puffback, clogged HX or clogged flue. Doesn't really matter since you are calling a pro now...right?0
as to why smoke would be coming from the top of the boiler. The optional rear or top flue is a great option on these. If it is rear flue, then the flue collector on top should be capped off with the supplied cover tightened. After the unit is fully serviced, and any ignition issues resolved, have the cover checked, The top is access to the flue passage ways.0
Good point Bill2,
I always replace the OEM gaskets on the flue collector after the first time I clean them because the gaskets don't hold you. They get hard and usually half stick to the boiler and flue collector. I use some Lynn rope which I glue to the top of the boiler with High Temp RTV and then slather the bottom of the flue collector with Never-Seize. So it comes off the next time. I clean a lot of WGO's. I've never had a problem with them once I do this fix.
You need to be very careful when putting them back. Put Never-Seize on all the bolts for ease of removal.
I cleaned a V-3 yesterday that was full of Kibble and Bits from being a cold start and 3" of K&B's piled up in the chamber. No Never Seize on the collector. Not good.
And it was cleaned by "someone else" since the install when the house was built before 2001. And serviced 11/09.
No one will ever convince me that a cold start boiler filled with Kibbles and Bits is more efficient than a warm start that has run for 2+ years and has only a brown ash/dust.0
This discussion has been closed.
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 771 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 625 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 17 Recall Announcements