Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Bullheaded T on return?
papadennis Member Posts: 3
I understand why a bullheaded T should not be used w/ hydronics. But, I'm wondering if one can be used on the RETURN. This would be two 1" runs going into a 1 1/4 bull. This configuration fits my boiler room set up.
For all the same reasons you wouldn't put it in the supply....
No. Water is like my ex-brother in law. Wet, lazy and stupid. Using bull headed tee's will produce those results. The path of resistance continually changes with bull headed tees and subsequently, the flow will also change continuously.
There are no less than 360 ways to use any fittings. :-) You can figure out a way to do it the correct way. You won't regret it.
MEIt's not so much a case of "You got what you paid for", as it is a matter of "You DIDN'T get what you DIDN'T pay for, and you're NOT going to get what you thought you were in the way of comfort". Borrowed from Heatboy.0
This discussion has been closed.
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 772 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 626 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 19 Recall Announcements