Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
most efficient piping of HW rads: "TIBO"
Manufacturer of my newly acquired Stelrad panel radiators recommends TIBO (top-in, bottom-out) supply-return piping config for each radiator. Says its 4% more efficient. My HVAC contractor says logic is that BITO or BIBO (bottom-in, top-out, or bottom-in, bottom-out) make more sense to him. Manufacturer says is a matter of the design of the rads and the pressure drop, that a unit extracts heat more efficiently; whereas contractor says that since heat rises, supply the bottom and the top takes care of itself. Average temp will be 135F.
A manufacture makes the product, tests the product and recommends the install of the product but the contractor who installs the product doesn't use their recommendations. Easy anwser what I would do. Find another contractor or have him install it per the manufacturers recommendations."The bitter taste of a poor installation remains much longer than the sweet taste of the lowest price."0
The same manufacturers
mounted the pumps on the return of their boilers for many years. Following anyone blindly is never a smart move. Most times they are correct but they are far from perfect. How many times has Triangle tube changed the inlet and outlet position on the phase three? Question everything!0
I think there are photos of rads
on the wall in infrared that show bottom in and bottom out is most even distribution of heat in a radiator. The hot water will displace the cold water best in this piping.Cost is what you spend , value is what you get.
cell # 413-841-6726
I wonder if they are looking at a constant circ application of tradition on/off situation?
i could see thermal siphoning helping out in an on/off control system.
They didn't say ...
Manufacturer supplies several generic piping diagrams (2 pipe; reverse return; series) and rad attachment option illustrations. They recommend 2 pipe and the illustration with TIBO configuration says: 4% more efficient. I assume that refers to the transfer of the heat from water to its emittance from the rads. They do suggest outdoor reset and room thermostates along with TRV's/panel.0
flat panel rads act like
some panel rads have vents like baseboards, so I could see where you would get a little more heat out if the top is hotter than the bottom. this would help the convection currents up through the panel.0
This discussion has been closed.
- 120.9K All Categories
- 83.8K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 415 Carbon Monoxide Awareness
- 34 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 114 Geothermal
- 154 Indoor-Air Quality
- 2.9K Oil Heating
- 49 Pipe Deterioration
- 745 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 619 Buy, Sell, Barter
- 37 Industry Classes
- 71 Job Opportunities
- 14 Recall Announcements