Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Two Maid O mist #1's vs Gorton #2?
How will these work on a main line vs a Gorton 2? I ask because A) I can get the maid O mist #1's or #D locally and B) I cant find a place that takes paypal over the net with gortons #2's. I can only pay payal, no Credit Card. :(
Venting capacity -
1 each Gorton # 2 is equal to almost 4 each Maid of the Mist #1
1 each # D is equal to 1 each Maid of the Mist #10
gerry gill Member Posts: 3,054well, like Rod says can you put
four of the #1's up there? that would be about what it would take to equal one #2 Gorton. If you were going to use gorton #2's would one vent be worth while?gwgillplumbingandheating.com
Serving Cleveland's eastern suburbs from Cleveland Heights down to Cuyahoga Falls.0
Wow, that big eh?
Right now my Mains are venting through some 1933's. So they are barely venting at all anything would be an improvement. I'll see if I can get the gortons.
Another thing is I have about 30 ft of 2.5" main lines (2 mains) in each direction, the vent is currently at the very end of the dry returns next to the boiler. Does it make more sense to have the vents on the end of the mains or end of the return? Or does this not matter so much?0
This discussion has been closed.
- 120.9K All Categories
- 83.8K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 416 Carbon Monoxide Awareness
- 36 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 117 Geothermal
- 154 Indoor-Air Quality
- 3K Oil Heating
- 49 Pipe Deterioration
- 754 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 622 Buy, Sell, Barter
- 37 Industry Classes
- 70 Job Opportunities
- 14 Recall Announcements