Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
markn Member Posts: 1
I'm having a hard time finding 1/4" angled vents for my radiators. All the vents I'm finding online have an 1/8" inlet or 1/4" straight. Can someone please let me know where I can find them and if there is more than one company that makes them which vent is better.
radiator air vents
try this site. have you tried cleaning the old ones? usually a soak in dishwashing liquid , and a shake can revive them. this is unfortunately not true for the main air vents which do all the work. i would invest in additional main vents first, and just clean the radiator vents. if you need to accomodate the 1/4 in, then just use a 1/4 X 1/8 bushing.--nbc0
I'll second the bushings
These will let you use standard vents. Brass bushings would be best. Amazingly, you can usually find 1/4"x1/8" brass bushings at Home Despot. Who'da thunk?All Steamed Up, Inc.
Towson, MD, USA
Steam, Vapor & Hot-Water Heating Specialists
Oil & Gas Burner Service
nbc - - how long
should a hoffman 1-A last? i've got a bunch i was going to replace, but am thinking of trying your cleaning method. but do they have a lifespan where beyond it, no amount of cleaning will assist? thx! jeff0
how deep is a well?
how long is a rope? they are pretty well made, and should last a long time.
if you can blow through the vents, and they close when steam has arrived, they are good to go.
i have had some hoffman vents for decades. as i said, they can only vent the riser and radiator, so they really never get subjected to the harsher conditions, in which the main vents operate. the radiator vents must never be expected to function as a substitute for the mains.otherwise, you will be paying the fuel company extra to remove the air, instead of letting it out through generous main vents.--nbc0
i have a rope...
but hopefully i won't be using it, because of all the excellent advice i'm getting here. i get it. light bulb went off when you said "including riser." steamhead set me straight on the main venting, so now i have my venting strategy firmed up. Thx!!0
This discussion has been closed.
- 120.9K All Categories
- 83.9K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 415 Carbon Monoxide Awareness
- 34 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 114 Geothermal
- 154 Indoor-Air Quality
- 3K Oil Heating
- 49 Pipe Deterioration
- 756 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 619 Buy, Sell, Barter
- 37 Industry Classes
- 70 Job Opportunities
- 14 Recall Announcements