Welcome! Here are the website rules, as well as some tips for using this forum.

# Air space between sub floor and finished floor

Options
Member Posts: 14
Hi,
Thanks for the info. I thought that the air gap would create a greater R value or that the bottom side of the plywood would reflect the heat back down which it may, but if there is enough insulation under the tube it will drive it up ?
I have another question. How do you know whether to put your tubing 16"cc or use 1/2" tube as to larger tube ?
I am going to order one of Dan's books on radiant but I need to know something before the book arrives.
Jay

• Member Posts: 14
Options

I am looking at a radiant job to bid. The owner wants a staple up job. The floor is not level, he wants to use sleepers to level the finished floor. I need to know how much that will reduce the efficiency of my tubing.So, I will staple to 3/4 inch old board floor then there will be from 1/4" to 1 1/2" dead air space then the plywood and finished floor, I'm not sure what the finished floor will be at this point. I do know enough to insulate well below the tubing to drive the heat up but what happens with the heat when it hits the bottom of the plywood and say carpet or hardwood over the plywood. It seems that we have lost the conductive value ????

Jay
• Member Posts: 506
Options
That air space

Jay, that air space will add (if captive and held by normal building materials) an additional R value of about 0.97.

Say your old board floor is 3/4" softwood (to which the tubing is attached), that has an R of 0.94, then the air space at 0.97, then plywood, (say another 3/4" AC softwood at 0.94 and then maybe a layer of rosin paper at 0.06 then 3/4" of finished hardwood at 0.68.

I do not discount the sleepers for they and the air space have about the same R value you see...

(Still with me? Jay? Jay? Wake up now...:)

I get a total R value of the floor assembly of 3.59.

(This does not include the interior air film coefficient of 0.68 but then I do not count that for radiant because it is about surface temperature.)

If you want a surface temperature of 80 degrees (24 BTUH per SF in a 68 degree room) your water temperature will be over 155 degrees...

• Member Posts: 178
Options
Floor buildup

Since you're already building up the floor, perhaps it would be best to look at using quicktrak, roth panels or warmboard instead of putting the tubing underneath? That will make for a much better system.

More insulation underneath is generally a good thing, but it won't do anything to overcome the high R value you have on top: you are still looking at really high water temps...
• Member Posts: 1,935
Options

1.) the plywood ready will not reflect heat back down.

2.) insulation really doesn't drive heat, it slows heat transfer, maybe a minor play with words.

did you do a heatloss on the room or rooms you plan to heat?

larger tubing can transfer more heat but doesn't conduct much more heat to the floor. -very,very small amount more.

the customer may want simple stable up, that doesn't mean it will work and you'll end up getting burned.
• Member Posts: 62
Options
why not do an overpour?

• Member Posts: 2,774
Options
It sounds like they do not have enough floor elevation for

overpour or quicktrak, he said the floor leveling for finish floor was between .25 & 1.5" that would not provide enough floor leveling and the above sub floor methods. That's what I got out of it? Tim
This discussion has been closed.