Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
steam radiator vents
Mark P. Legassey Member Posts: 3
I have new Vent-Rite air vents and on the bottom of them are white turnable knobs. numbered from 1 to 9. how do i interperte the numbers, and what do they mean?
Open to Closed, Faster to Slower
The higher the number, the faster it will vent, the lower the number, the slower it will vent.
Typically, this adjustment is used in conjunction with other similar radiator vents or other vents of any type, to regulate how fast air gets out and how fast steam gets in.
For the matter at hand, I am glad that they are all the same and all adjustable.
You want all of your radiators to get hot at the same time, ideally, so the radiators closest to the boiler will get a lower number setting and the furthest ones a higher number setting.
Adjust them sparingly, meaning wait a few hours and a few cycles between re-adjustments. Once you get them all working together, leave them alone. I would start with all on "5", the mid-point, and adjust from there. Your perceived distance and the actual time for steam delivery may be different.
Oh, while we are at this, make sure that you have generously (read: properly) sized main vents. Do not make these new vents work to hard.
Do not be mis-lead by the "Spinal Tap" vents. That is a hoax. There is no "11"0
This discussion has been closed.
- 120.9K All Categories
- 83.8K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 415 Carbon Monoxide Awareness
- 34 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 114 Geothermal
- 154 Indoor-Air Quality
- 2.9K Oil Heating
- 49 Pipe Deterioration
- 745 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 619 Buy, Sell, Barter
- 37 Industry Classes
- 71 Job Opportunities
- 14 Recall Announcements