Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Boiler firing too often during summer
the aquastat on the indirect, or perhaps get rid of it and control through an actual boiler control.It sounds like the diferential is set to close it should be above 5 degrees no less.