Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
correct radiator piping?
Thanks for your comments. Will the TBSE method work for a 6' long radiator, too. I'm thinking that the water will short cycle and only heat one end.
Correct radiator piping? When piping a hot water radiator, where is the best place to connect the two pipes? I think that connecting to the bottom on each side, but some say bottom on one side and top on the other side. The radiators we,re installing are going in a basement and the pipes are comming from above. I,d appreciate your comments. Thank you0
It doesn't really matter. Hot water rises, so it is best to put the output at the bottom (take colder water away), but no matter where the input is, hotter water will float to the top anyway. Of course, given a reasonable flow rate, there's a good bit of mixing, which is why it is not worth worrying about.0
I installed the radiators in my own house using the TBSE method, meaning top and bottom same end. If you choose this method, I would recommend supplying the top of the radiator and returning from the bottom. I tried supplying the bottom and returning from the top at first. About one third of most of the larger radiators did not seem to heat.0
My 4' radiator works fine with this configuration, 6' should not be a problem either.0
This discussion has been closed.
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 772 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 625 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 19 Recall Announcements