Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
If the odor is ONLY in the HOT water, then you probably have a tank type water heater with a magnesium anode rod. You would need to replace the magnesium rod with an aluminum/zinc rod, and disinfect the tank and hot water piping with hydrogen peroxide.
If the odor is in both the cold and hot water, then it needs to be adressed from the well.