Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contactus/.
Click here to Find a Contractor in your area.
measure flow rate
ALH_4
Member Posts: 1,790
If you know the flow and deltaT on one side of the heat exchanger, you know how much heat is being transferred. Then if you have the deltaT on the other side of the heat exchanger, you can calculate the flow rate from the heat transfer on the other side and deltaT on that side using GPM=(heat transferred)/(500*dT) For glycol solution, apply a coefficient (given by the manufacturer) to the "500" to account for reduced heat capacity. It would be somewhat approximate, but probably pretty accurate. It just saves the cost of installing two flow meters, but if the cost of the extra meter is not a concern, two would be nice. Also verify the accuracy of the rotameter design for the viscosity of the glycol solution. The Pentair meters should be ok for up to 50% glycol solution above 70°F or so.
0
Comments

measure flow rate
is there a gauge to measure the flow rate into a heat exchanger? I ordered one which will just meet my requirements if I can keep my flow rates at or below 2 gpm0 
Without the special fittings...
that have gage taps across the fitting, it is hard; but not impossible.
What tool did you order?
To Learn More About This Professional, Click Here to Visit Their Ad in "Find A Professional"0 
I meant I ordered a flat plate heat exchanger that just met my requirements. That' why I want to measure the flow rate. It had to be 22.5 gpm on either side to get the output I need.0 
Flow
Would a higher flow rate not work with a smaller deltaT? Are you trying to maintain a particular outlet temperature?
Pentair makes good rotometers to measure flow rates accurately. The nice part is, with four thermometers and one flow meter, you can tell the flow rates on each side (by backing out the flow from the deltaT on the flowmeterless side) and heat transfer at any moment.0 
the Flat Plate exchanger I bought doesn't leave me any wiggle room with flow rates. I've entered many different variables in the design conditions but it only seems to work with 22.5 gpm. I like your idea of 4 temp gauges and a flow meter. I'll check that link you sent. Thanks0 
Andrew, could you elaborate a bit more on how to set up the flow meter and temp gauges so as to measure flow on either side? I'm not sure what you mean by "backing out the flow from the delta T"0 
I understand now. thanks for taking the time to explain.
Peace, Tom0
This discussion has been closed.
Categories
 All Categories
 85.2K THE MAIN WALL
 3.1K AC, Heat Pumps & Refrigeration
 55 Biomass
 424 Carbon Monoxide Awareness
 73 Chimneys & Flues
 1.9K Domestic Hot Water
 5.2K Gas Heating
 129 Geothermal
 160 IndoorAir Quality
 3.3K Oil Heating
 61 Pipe Deterioration
 884 Plumbing
 5.9K Radiant Heating
 376 Solar
 14.7K Strictly Steam
 3.2K Thermostats and Controls
 58 Water Quality
 49 Industry Classes
 89 Job Opportunities
 28 Recall Announcements