To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
no header and equalizer???
i went on estimate today, it was a leaking steam boiler . boiler must be replaced. radiation equals to 325 sq ft/78,000 btus. i got job going to replace tomorrow morning. question is existing boiler has one 3" inch going strainght up to a 2" inch main, no header no equalizer no hartford loop return just goes straight into boiler return tapping. system is a one pipe gravity return system , correct me if im wrong i think its a parellel flow sytem, at the ends of the 2 mains there is a main vent then it drops down to 1 inch 1/4" , should i pipe like i normally do ?, drop header, and how did it work for the last 20 years? no check valve on return...thanks paul s
0 · ·