To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Reducing Coupling on Two Upstairs Radiators at end of run causing Problems?
Two upstairs radiators on the far end of the run have reducing fittings from the normal size hot water pipe feeding the radiators of appoximately one inch plus or minus down to maybe a half inch copper pipe.
It took awhile for the last radiators on top and bottom floors to get hot recently and wonder if that reduction impedes the flow of water and the circulation of the hot water to those radiators and others in house when there is a call for heat?
Old Delco Boiler, Beckett AF, 2 family house, burner recently tuned up.