To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Weil McLain vent pipe freezing side wall
Weil McLain gv4 series 2 boiler. Side wall termination intake freezing. This direct vents out 3 inch PVC. Has their side wall cover. Intake and exhaust flat plate intake through sides and exhaust out hole. Their no condensation drain near the boiler vent pipes or from bottom of boiler. This is main problem I can get over. Some manual says it stays over 130 to reduce condensation, but isn't their still some condensate that needs to drain. I am helping out over phone and this doesn't seam right. Altitude is 4850. Any boiler experts in Bozeman MT for service? Any thoughts about the gv4 series 2 not having condensate drain. They are new to the house this year. I am worried about no drain hooked up, possible co leaking from drain port if not hooked up. Thanks for thoughts
0 · ·