To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
overcome excess edr. See attachment. Steam guy doesn't want to replace pipes with larger pipes, feels it's too invloved, suggests re-routing lateral B off branch to new branch off main. Connected EDR to current branch(A) is 82, the laterals are 3/4" except for C which is 1". By doing so connected EDR to A would be reduced to 44, with 38 connected to propose piping. Reason for seeking a fix is that only rad off C heats well at all times, other 3 will heat together if valves on rads off B are opened slightly, and rad on D opened all the way, however, rads off B will heat minimally, and D slightly better. If the rad off B are opened more, then D doesn't heat. Any feedback appreciated.