To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
The new house I bought has both radiant and baseboard heating currently installed. After doing some research I've discovered that the radiant heat portion isn't hooked up correctly and is cheaply rigged once it leaves the boiler ( no manifolds, uses same water temp as baseboard, etc.)
Here's a drawing of the current set up along with an actual picture.
I've also attached what I believe would be close to the new setup. I'm not sure if I'm missing anything so I could use some help.
One question I do have on my "new design" . Would I need two expansion tanks, one for the boiler side and one on the zone side?
Thanks ahead of time for any input.